Home || Diesel engines
||Steam turbines ||Fuel treatment ||Pumps ||Valves ||Refrigeration ||
Direct current supply, distribution, D.C. generators field connection & earth lamp circuit
How a D.C. current is produced ?:
A current is produced when a single coil of wire is rotated in a magnetic
field. When the current is collected using a ring which is split into two
halves (a commutator), a direct or single direction current is produced.
The current produced may be increased by the use of many turns of
wire and additional magnetic fields.
With many coils connected to the commutator, sparking will occur as
the current collecting brushes move across the insulated segments.
Commutating poles or interpoles are used to reduce this sparking. They
are in fact electromagnets having a polarity the same as the main pole
which follows in the direction of rotation.
The magnetic field between the poles is produced by what are known
as 'field coils'. These coils are excited or energised by the current
produced in the machine.
The soft iron core of the field coils retains
some magnetism which enables a preliminary current generation to
build up eventually to the full machine output. The field windings can
be connected to the output current in a number of waysóshunt, series
or compound. The compound wound arrangement is usual since it
provides the best voltage characteristics.
Fig:D.C. generators field connection
The compound wound generator has two sets of field coils .
The shunt coil has many turns of fine wire and the series coil
has a few turns of heavy wire. The shunt field produces full voltage on
no-load which falls off as the load current increases. The series field
creates an increase in voltage as the load increases. Properly combined
or compounded the result is a fairly constant voltage over a range of
load (Figure below).
Fig:D.C. generators characteristic curves
Direct current distribution
The generated supply is provided to conductors known as 'bus-bars'
which are located behind the main switchboard. The supply then passes
through circuit breakers to auxiliaries directly or to section or
distribution boards. A circuit breaker is an isolating switch. A section
board is a grouping of electrical services fed from the main board. A
distribution board feeds minor supplies such as lighting and may itself
be fed from the main board or a section board. The distribution system
is shown in diagram
A two wire system is usual to provide a supply and return to each item
of equipment. An earth lead would be the only electrical connection
between any item of equipment and the ship's structure. With
compound wound generators a third bus-bar would be introduced as the
equalising connection between machines.
A fuse is a type of switch which isolates a circuit if an excessive current
flows. To reconnect the circuit, after discovering the cause of the
overload, the fuse must be rewired or replaced. The fuse is in effect a
weak link in the circuit designed to break and protect equipment from
damaging high currents. A semi-enclosed or rewirable fuse will have
provision for a wire to be replaced after it has burnt out. The correct
rating of fuse wire should be replaced within the holder to reinstate the
circuit. A cartridge fuse has the wire enclosed within a ceramic body and
it is not rewirable. A 'blown' cartridge fuse must be replaced by a new
one, The cartridge fuse is to be preferred since the fusing current value
is more reliable than for a rewirable type.
A circuit breaker is an isolating switch which also functions as a fuse. It
has two designed ratings: one of the normal safe working current, the
other the overload current. The breaker is closed against the action of a
spring to make the circuit and supply the section board or auxiliary. A
trip mechanism opens the breaker, a fast opening being ensured by the
spring. When desired the breaker is tripped or opened manually. It will
also open if the overload current rating is exceeded for a period of time.
A delay mechanism prevents the breaker opening for short-period
overload currents. The circuit breaker opens or closes both supply and
return leads in the circuit. Where a circuit breaker feeds the generator
supply to the bus-bars a third 'make-or-break' arm will be provided for
the equaliser connection.
Preferential tripping is a means of retaining essential electrical
supplies. In the event that a generator cannot supply all the load then
non-essential loads are disconnected by preferential trips. The intention
is to reduce the generator load while ensuring essential equipment such
as steering gear, navigation lights, etc., retains its electrical supply.
Various circuit faults can occur as a result of either a break in the
conductor (cable) or a break in the insulation. An open-circuit fault
results from a break in the conductor and no current flow will take place,
A short-circuit fault is due to two breaks in the insulation on, for
example, adjacent conductors. The two conductors are connected and a
large current flow takes place. An earth fault occurs when a break in the
insulation permits the conductor to touch an earthed metal enclosure (or
Fig:D.C. generators Earth lamp circuit
Earth faults are usually detected by the use of earth indicating lamps.
Two lamps are used, each rated for the full system voltage, but
connected in series across the system with the mid point earthed , If the system is correctly insulated then both lamps will glow at
half brilliance. The lamps are placed close together to enable a
comparison to be made. A direct earth in one pole will short circuit its
lamp, causing the other to shine brighdy. A slight insulation breakdown
would produce a difference in bulb brightness between the two. Where
an earth fault is detected the circuit breakers for each separate circuit
must be opened in turn until the fault location is discovered. The
particular section or distribution box would then have to have its circuits
investigated one by one to locate the fault and enable its correction.
Direct current supply
The supply to a distribution system will usually come from two or more
generators operating in parallel. Each generator must be provided with
certain protective devices to ensure against reverse currents, low voltage
or an overcurrent. There must also be ammeters and voltmeters in the
circuits to enable paralleling to take place.
Fig:Protective trips for the parallel operation of two d,c. generators
The circuit for two generators operating in parallel is shown in Figure
above. A triple-pole circuit breaker connects the supply to the bus-bars and
also the equaliser bus-bar. The arrangement of the various protective
trips can be seen, with excess current protection being provided in each
pole. The reverse current trip prevents the generator operating as a
motor if, for instance, the prime mover stopped.
The voltmeters and ammeters are provided in the generator supply
circuits for paralleling purposes. A voltmeter is positioned across the
bus-bars to indicate their voltage. Consider the situation where one
generator is supplying the bus-bar system and a second generator is to
be paralleled with it. The second machine is run up to speed and its field
current adjusted until the two machines are at the same voltage. The
circuit breaker connecting the second machine to the bus-bar can now be
closed and the Field current adjusted to enable the generator to take its
share of the load. When the load is evenly shared the two machines can
then be left to operate in parallel. The equalising connection will cater
for any slight changes in load sharing that occur.
- A.C. motors for ships machinery
Supplying alternating current to a coil which is free to rotate in a magnetic field will not produce a motor effect since the current is constantly changing direction. Use is therefore made in an induction or squirrel cage motor of a rotating magnetic field produced by three separately phased windings in the stator. ...
Use of A.C. generatorsA coil of wire rotating in a magnetic field produces a current. The current can be brought out to two slip rings which are insulated from the shaft. Carbon bushes rest on these rings as they rotate and collect the current for use in an external circuit. Current collected in this way will be alternating, that is, changing in direction and rising and falling in value. To increase the current produced, additional sets of poles may be introduced....
D.C. motors for ships machinery When a current is supplied to a single coil of wire in a magnetic field a force is created which rotates the coil. This is a similar situation to the generation of current by a coil moving in a magnetic field. In fact generators and motors are almost interchangeable, depending upon which two of magnetic field, current and motion are provided.....
Use of D.C. generatorsA current is produced when a single coil of wire is rotated in a magnetic field. When the current is collected using a ring which is split into two halves (a commutator), a direct or single direction current is produced. The current produced may be increased by the use of many turns of wire and additional magnetic fields....
Emergency power supply for ships machinery operation
In the event of a main generating system failure an emergency supply of electricity is required for essential services. This can be supplied by batteries, but most merchant ships have an emergency generator. The unit is diesel driven and located outside of the machinery space .
Maintenance requirement for ships electrical equipment
With all types of electrical equipment cleanliness is essential for good operation. Electrical connections must be sound and any signs of sparking should be investigated. Parts subject to wear must be examined and replaced when necessary. ...
Choice of batteries for ships machinery spaces - Lead acid and alkaline batteries
The battery is a convenient means of storing electricity. It is used on many ships as an instantly available emergency supply. It may also be used on a regular basis to provide a low-voltage d.c. supply to certain equipment.....
Ships battery maintenance guidance The electrolyte level should be maintained just above the top of the plates. Any liquid loss due to evaporation or chemical action should be replaced with distilled water. Only in an emergency should other water be used. It is not usual to add electrolyte to batteries.....
Operating characteristics of battery for ships machinery spaces
Having been 'discharged' by delivering electrical power a battery must then be 'charged' by receiving electrical power. To charge the battery an amount of electrical power must be provided in the order of the capacity.....
Insulation resistance measurement
Good insulation resistance is essential to the correct operation of electrical equipment. A means must be available therefore to measure insulation resistance. Readings taken regularly will give an indication as to when and where corrective action, maintenance, servicing, etc., is required....
Use of navigational light circuitsThe supply to the navigation lights circuit must be maintained under all circumstances and special provisions are therefore made. To avoid any possibility of accidental open circuits the distribution board for the navigation lights supplies no other circuit.....
WardóLeonard speed control system
As a very flexible, reliable means of motor speed control the Ward-Leonard system is unmatched.The system is made up of a driving motor which runs at almost constant speed and powers a d.c. generator .....
- Danger of electric shock to human bodyThe resistance of the human body is quite high only when the skin is dry. The danger of electric shock is therefore much greater for persons working in a hot, humid atmosphere since this leads to wetness from body perspiration.....
Marine machineries - Useful tags
Marine diesel engines ||Steam generating plant ||Air conditioning system ||Compressed air ||Marine batteries ||Cargo refrigeration ||Centrifugal pump ||Various coolers ||Emergency power supply ||Exhaust gas heat exchangers ||Feed system ||Feed extraction pump ||
Flow measurement || Four stroke engines || Fuel injector || Fuel oil system || Fuel oil treatment ||Gearboxes || Governor ||
Marine incinerator ||
Lub oil filters ||
MAN B&W engine ||
Marine condensers ||
Oily water separator ||
Overspeed protection devices ||
Piston & piston rings ||
Crankshaft deflection ||
Marine pumps ||
Various refrigerants ||
Sewage treatment plant ||
Starting air system ||
Steam turbines ||
Steering gear ||
Sulzer engine ||
Turbine gearing ||
Two stroke engines ||
UMS operations ||
Drydocking & major repairs ||
Critical machinery ||
Deck machineries & cargo gears
|| Control and instrumentation
||Engine room safety ||
Machinery Spaces.com is about working principles, construction and operation of all the machinery
items in a ship intended primarily for engineers working on board and those who working ashore . For any remarks please
Copyright © 2010-2016 Machinery Spaces.com All rights reserved.
Terms and conditions of use